Platinum Split Twin
3000 Cubic Feet
- Dual evaporators
- Greater cooling capacity
- Advanced electronic control system
- 3-speed fan switch to adjust BTU/h capacity
- Standard and 24V thermostat options are available
- Condensing unit can be placed outdoors with the purchase of exterior housing
- 55ºF temperature differential between the cellar and condensing unit air intake temperature
- Suitable for temperatures as low as -15F to 110F
- KDT Digital Controller/Thermostat with 50-ft. cable
- 220V High Efficiency (H.E.) Condenser Option
The Platinum Split Twin was designed to cool wine cellars needing a larger capacity unit. Described in the simplest terms, a split system is a cooling unit wherein the evaporator unit and condensing unit have been “split” into two separate units instead of being contained within the same housing. The evaporator unit is located in or near your cellar, and the condensing unit is generally located outside, or in an attic or utility room.
The Platinum Series of split systems allow you to decide where the evaporator unit and the condensing unit will be located. The condensing unit can be located up to 100 ft. away from the evaporator unit. The evaporator unit will be mounted in the cellar or it can also be located nearby with ducting.
If you don’t mind seeing the grille of your cooling unit in your cellar, a wall-mounted split system is what you need. If you prefer your unit to be out of sight, you should get a fully ducted split system. The choice is yours.
Not sure if the Platinum Split is suitable for your wine cellar? Call 800-323-3130.
Note: A qualified HVAC-R technician is required for installation. Failure to install the system by a qualified technician will void the warranty.
*PLEASE NOTE: WhisperKOOL does not provide a smart thermostat. By selecting the 24V Thermostat Conversion Kit, you have acknowledged that the system will not be built with the standard WhisperKOOL control or liquid measuring bottle probe. To run the equipment, you will have to source and purchase your own 24V smart thermostat. The WhisperKOOL Customer Satisfaction Team does not provide technical support for smart thermostats.
7850 – 8054
The BTU/h value range shown here is a theoretical number. There are often circumstances under which a cellar design may require a larger unit due to variables not accounted for in the formula. For example, these variables could be building materials (such as glass, stone, concrete, etc.) that do not offer the insulation capacity required to maintain the optimal cellar environment. We recommend purchasing a unit with a larger capacity to compensate for these unaccounted-for variables. An undersized unit can lead to premature failure and will most likely prevent the cellar from reaching your desired temperature
Cellar Size 3000cu. ft.*
BTU/h (85°F condenser air intake temperature)
Medium: 7850 • High: 8164
CFM 200 Per Unit
Dimensions Evaporator: 16.1”L x 20.5”W x 15.5”H • Condenser: 16.08”L x 16.23”W x 16.16”H
Voltage Reading Evaporator: 115V (15 amp dedicated circuit required) • Condenser: 230V (15 amp dedicated circuit required
Weight (lbs) Evaporator: 57 • Condenser: 67
Amps Evaporator: Evaporator: 1 (running amps) • Condenser: LRA 50/RLA 9.3
Line Set Liquid Line 3/8” • Suction Line (Less than 50ft. 3/4”) (Greater than 50ft. 7/8”)
Drain Line ½” ID clear plastic tubing (not provided)
Installation Evaporator is installed in the cellar. Condensing unit can be installed up to 100 line feet from the evaporator unit.
Thermostat Advanced digital display (50ft. cable), liquid-temperature-measuring bottle probe (retractable cable)
Temp. Delta: Can maintain a 55°F cellar temperature with up to 110°F condenser air intake temperature
Warranty: Two-year limited warranty (parts and labor)
Options: Exterior condenser housing, 24V thermostat conversion kit, condenser coil coating
3000 cubic feet
Fan Speed Medium/ High
BTU/h (60°F condenser air intake temperature) 7817 / 8015 Sensible / Total
BTU/h (75°F condenser air intake temperature) 7420 / 7868 Sensible / Total
BTU/h (85°F condenser air intake temperature) 7083 / 7657 Sensible / Total
dBA 42 / 46
Dimensions 22.1”L x 22.5”W x 15.5”H
Voltage Rating 120V (15-amp dedicated circuit required)
Weight (lbs) 54
Amps Primary 2.48 (Running Amps) ; Secondary (2.2 Running Amps)
Drain Line 1/2″ ID clear plastic tubing (not provided)
Installation Evaporator unit is installed in the cellar.
Thermostat Advanced digital display (50-ft cable), liquid-temperature-measuring bottle probe (retractable cable), 24V -customer supplied
Temp. Delta Can maintain a 55°F cellar temperature with up to 120°F condenser air intake temperature
Warranty Two-year limited warranty (parts and labor)
Dimensions 31.18″L x 10.75″W x 21.18″H
Condensing Unit 1 HP
Voltage Rating 220V (15 Amp Dedicated Circuit)
Weight 64 lbs
AMPS LRA 20A, RLA 4.25A, FLA 4.89A
Line Set Liquid Line 3/8″OD; Suction Line 5/8″OD (less than 50′),(3/4″ greater than 50″)
Installation Condensing unit can be installed up tp 100 line feet from Evaporator Unit
Temp Delta Can Maintain a 55 degree Cellar Temperature with up to 120-degree condenser intake temperature
Warranty 2 years limited warranty (parts and labor)